Simulation investigation on solar powered desiccant coated heat exchanger cooling system
Solar powered solid desiccant cooling system is a good alternative to conventional vapor compression system. In this paper, a novel solar driven desiccant coated heat exchanger cooling (SDCC) system is proposed. In order to validate the feasibility of such system and to predict system performance, an integrated system model is established by combing the mathematical models of different components. The model is adopted to evaluate system performance under Shanghai summer condition with high temperature as well as high humidity ratio. It is found that SDCC system can provide satisfied supply air to conditioned indoor space from 8:00 to 17:00 in June and July, the biggest cooling powers are 2.9kW and 3.5kW, and corresponding solar COP are 0.22 and 0.24 respectively. In August, the system needs relatively short switch time (less than 2min) to provide satisfied supply air, and the corresponding cooling power can reach to 5kW. To make a good compromise between system performance and system constitution, 2min is recommended as the switch time under simulated condition in August. Also, effects of main design parameters on system performance are calculated and discussed.
If you experience problems downloading a file, check if you have the proper application to view it first. In case of further problems read the IDEAS help page. Note that these files are not on the IDEAS site. Please be patient as the files may be large.
As the access to this document is restricted, you may want to look for a different version under "Related research" (further below) or search for a different version of it.
Volume (Year): 93 (2012)
Issue (Month): C ()
|Contact details of provider:|| Web page: http://www.elsevier.com/wps/find/journaldescription.cws_home/405891/description#description|
|Order Information:|| Postal: http://www.elsevier.com/wps/find/journaldescription.cws_home/405891/bibliographic|
References listed on IDEAS
Please report citation or reference errors to , or , if you are the registered author of the cited work, log in to your RePEc Author Service profile, click on "citations" and make appropriate adjustments.:
- Enteria, Napoleon & Yoshino, Hiroshi & Satake, Akira & Mochida, Akashi & Takaki, Rie & Yoshie, Ryuichiro & Baba, Seizo, 2010. "Development and construction of the novel solar thermal desiccant cooling system incorporating hot water production," Applied Energy, Elsevier, vol. 87(2), pages 478-486, February.
- Ge, T.S. & Dai, Y.J. & Wang, R.Z. & Peng, Z.Z., 2010. "Experimental comparison and analysis on silica gel and polymer coated fin-tube heat exchangers," Energy, Elsevier, vol. 35(7), pages 2893-2900.
- Eicker, Ursula & Schneider, Dietrich & Schumacher, Jürgen & Ge, Tianshu & Dai, Yanjun, 2010. "Operational experiences with solar air collector driven desiccant cooling systems," Applied Energy, Elsevier, vol. 87(12), pages 3735-3747, December.
When requesting a correction, please mention this item's handle: RePEc:eee:appene:v:93:y:2012:i:c:p:532-540. See general information about how to correct material in RePEc.
For technical questions regarding this item, or to correct its authors, title, abstract, bibliographic or download information, contact: (Dana Niculescu)
If you have authored this item and are not yet registered with RePEc, we encourage you to do it here. This allows to link your profile to this item. It also allows you to accept potential citations to this item that we are uncertain about.
If references are entirely missing, you can add them using this form.
If the full references list an item that is present in RePEc, but the system did not link to it, you can help with this form.
If you know of missing items citing this one, you can help us creating those links by adding the relevant references in the same way as above, for each refering item. If you are a registered author of this item, you may also want to check the "citations" tab in your profile, as there may be some citations waiting for confirmation.
Please note that corrections may take a couple of weeks to filter through the various RePEc services.